Goto Section: 15.111 | 15.115 | Table of Contents
Revised as of October 1, 2014
Goto Year:2013 |
§ 15.113 Power line carrier systems.
Power line carrier systems, as defined in § 15.3(t), are subject only
to the following requirements:
(a) A power utility operating a power line carrier system shall submit
the details of all existing systems plus any proposed new systems or
changes to existing systems to an industry-operated entity as set forth
in § 90.35(g) of this chapter. No notification to the FCC is required.
(b) The operating parameters of a power line carrier system
(particularly the frequency) shall be selected to achieve the highest
practical degree of compatibility with authorized or licensed users of
the radio spectrum. The signals from this operation shall be contained
within the frequency band 9 kHz to 490 kHz. A power line carrier system
shall operate on an unprotected, non-interference basis in accordance
with § 15.5 of this part. If harmful interference occurs, the electric
power utility shall discontinue use or adjust its power line carrier
operation, as required, to remedy the interference. Particular
attention should be paid to the possibility of interference to Loran C
operations at 100 kHz.
(c) Power line carrier system apparatus shall be operated with the
minimum power possible to accomplish the desired purpose. No equipment
authorization is required.
(d) The best engineering principles shall be used in the generation of
radio frequency currents by power line carrier systems to guard against
harmful interference to authorized radio users, particularly on the
fundamental and harmonic frequencies.
(e) Power line carrier system apparatus shall conform to such
engineering standards as may be promulgated by the Commission. In
addition, such systems should adhere to industry approved standards
designed to enhance the use of power line carrier systems.
(f) The provisions of this section apply only to systems operated by a
power utility for general supervision of the power system and do not
permit operation on electric lines which connect the distribution
substation to the customer or house wiring. Such operation can be
conducted under the other provisions of this part.
[ 54 FR 17714 , Apr. 25, 1989; 54 FR 32339 , Aug. 7, 1989; 75 FR 63031 ,
Oct. 13, 2010]
return arrow Back to Top
Goto Section: 15.111 | 15.115
Goto Year: 2013 |
CiteFind - See documents on FCC website that
cite this rule
Want to support this service?
Report errors in
this rule. Since these rules are converted to HTML by machine, it's possible errors have been made. Please
help us improve these rules by clicking the Report FCC Rule Errors link to report an error.
Helping make public information public